Liquid for filling only the latest generation of thermal systems: "Ion Master" and "Comfort Ion Master" (systems with heat exchangers - the primary systems).
The concentration of the liquid is dependent on the type of boiler in the thermoblock system (special concentration for each power of boiler/heater). In order, the customer must accurately indicate the power of the boiler for which FE-1 fluid is required.
LIQUID FOR FILLING A SYSTEM WITHOUT HEAT EXCHANGER (PRIMARY AND SECONDARY SYSTEMS)
Propylene glycol FE-3 is used in systems without heat exchanger. Propylene glycol FE-3, as well as Propylene glycol FE-1, contains precisely balanced additives that protect ionizing heating systems from negative effects. After many years of testing and numerous experiments in the development sector of the company "Ekoterm 2001", the completely ecological Propylene glycol FE-3 liquid was created. This fluid is being delivered to customers in 100% concentrated state, in 10L packages. Before filling the system, the Propylene glycol FE-3 must be diluted with distilled water only, in the ratio of 1:1,5, which means that 15 liters of distilled water must be mixed with 10 liters of Propylene glycol FE-3. This ratio must be precise (1: 1,5), so as not to disturb the balance of additives in the system. Propylene glycol FE-3 cannot be mixed with any other fluid, or any water other than distilled one. When filling the fluid into the system (due to eventual pressure drop after some time of system using), Propylene glycol FE-3 must also be re-inserted, as well as diluted in the ratio of 1: 1,5 (1L Propylene glycol FE-3 to 1,5L of distilled water).
Any different mixing ratio will not give satisfactory results.
Another solution created in the production of the company "Ekoterm2001" - Serbia!
There is no more complicated and long-term adjustment of electrolytes in systems with ionizing boilers.
Advantages of the electrolyte adjustment dozer:
Special dosing systems for ionizing electrode boilers, created in the development sector of the company "Ekoterm2001" - Serbia, are unique in the world. A very simple option for adjustment of the electrolyte in the system with extreme precision, without any effort and very complicated setting. You can also set up the system yourself by simply following the technical instructions. You don’t need expensive central heating installers for this anymore.
Dosing system is used in latest generation of thermoblocks.
About 20 milliliters is enough for one system dosing. The FE-2 has all the features of “Propylene glycol FE-1“ and is completely environmentally safe. The FE-2 electrolyte dosing liquid is used for setting up amperage, even to a precision of 0.1 ÷ 0.2 A.
You can buy Electrolyte FE-2 only in the company "Ekoterm 2001". It is the only and safe way to get the original fluid for adjusting electrolytes.
Filter is necessary in ionizing systems to retain particles of impurities that prevent proper operation of the boiler. During the heating season clean the filter if necessary.
Advantages of heat exchangers:
Special heat exchangers for ionizing boilers, unique in the world!
Special heat exchangers serve primarily to transfer the heat from the primary to the secondary ionizing heating system, where exceptional system purity is required. Exchangers are constructed from special materials that cannot be contaminated by the heating system. This solution took years of research and experiments. The company "Ekoterm2001" has innovated and placed on the world market several kinds of heat exchangers, depending on the power, which are without any competition in the world of thermal-technics. Since standard exchangers cannot work in ionizing systems, because there is a large amount of dirt, corrosion, high power consumption and blockage of the system's work, Ekoterm2001 has designed this unique solution. Traditional heat exchangers that can be found on the market are made according to completely different standards in relation to ionizing heat exchangers and cannot be used adequately in ionizing heating. Ionizing heat exchangers can be used in all heating systems, both in the ionizing and the standard systems.
"Afifer A-1" is a biodegradable cleaner for the central heating system, which removes all impurities and other undesirable elements inside the system. Removes milder forms of corrosion, stones, grease, etc.
"Afifer A-1" is a completely ecological fluid and it is completely adapted to clean ionizing systems. It can be used for rinsing other heating systems as well. "Afifer A-1" must be diluted with water in the range of 2 ÷ 3%. If the systems are very dirty (corrosion, stones, etc.), a stronger concentration of bio-cleaner "Afifer A-1" can be dosed (up to 5%), the procedure can be repeated several times depending on the impurities in the system, since this liquid doesn’t cause harmful effect on heating systems. Rinsing with "Afifer A-1" takes about an hour. During this time, the circulation pump must be at the maximum speed. While the system is being rinsed, do not turn on the heater (turn on the circulation pump only). After one hour of rinsing with "Afifer A-1", wash the system with clean water. If necessary, repeat the procedure until completely clean water comes out of the system. After that, you can access the system filling.
"Afifer A-1" can be purchased exclusively in "Ekoterm 2001" sales. It is the only and safe way to get to the original rinsing liquid. Other rinsing liquids are not suitable for the ionizing systems. For any other information, read the technical manual for the installation of the thermoblock system.
"Afifer A-1" is supplied in 1 liter packages.
The cartridge filter is used for fine filtration of the fluid in the system from mechanical impurities. Wash the filter cartridge during system operation if necessary, or replace it with a new cartridge in case it is too dirty and cannot be adequately washed off. Rinse the cartridge by placing it under the running hot water.
FE-2 fluid for electrolyte dosing in the system is being used where no heat exchanger is present. FE-2 is being dosed with about 20 ÷ 25 ml of liquid on every 10L of distilled water in the system. A bit more of FE-2 fluid can be added if necessary. The FE-2 fluid is used to increase the heating power in ionizing systems.